SGS Baseefa - New Edition of<br /> EN 14986:2017
Design of fans working in potentially explosive atmospheres” – the impact on industry
The new edition was issued in January and, although not greatly different in principle from the 2007 edition, there are enough changes to mean that most fans will have to be reassessed against the new standard before the 2007 edition loses its harmonisation status, probably in January 2020. Read the full newsletter for more information.
The following points are noted:
- For the first time, the new standard recognises that the heat loss from an electric motor that is in the fluid stream might be relevant in allocating the Temperature Class.
- To match permitted reductions in rotational clearances, there are enhanced requirements on the rigidity of the fan casing, and a greater emphasis on the ability to measure rotational clearances during routine maintenance. But the possible causes of casing distortion are treated with more care, including requiring that the installation and commissioning instructions should have a section detailing the maximum permitted loads to be imposed on the casing by any connected ductwork. Although many manufacturers may currently provide this information, there remains the possibility that this will also mean more work for fan installers.
- In view of the greater emphasis on maintaining mechanical clearances, a relaxation has been permitted on materials of construction in that, for Category 3 fans up to a certain size and speed, it is no longer obligatory to meet the requirements for “spark resistant” material pairings. Alternatively, for the same sizes of fan, if the accepted material pairs are used, it is not necessary to make provision for clearance measurement during routine maintenance. Neither relaxation applies to Category 1 or Category 2 fans.
- The tables on permitted material pairings have been totally reconstructed. Most of the data remains unchanged, but it is difficult to compare the old and new tables as the previous notes following the table are now incorporated directly in the table, and the order changed. For example, the original Table 2 with separate notes comprised two pages. The new table, without separate notes, now takes six and a half pages, but requires less “back and forth” reading.
- The five sub-clauses relating to: shaft seals; bearings; power transmissions; clutches and couplings, and braking systems, now no longer restrict the protection concept to “constructional safety”, but overtly recognise “liquid immersion” and “control of ignition sources” as valid methods of protection. The use of “control of ignition sources” – such as by incorporating thermal or vibration monitoring – is generally becoming more popular for many types of non-electrical equipment, so incorporation in the fan standard is welcome.
- To match the enhanced requirements on rigidity, there are now enhanced requirements relating to the securing of the fan impellor to the shaft. The previous quarter page is extended to four pages, with drawings, making the requirements clearer.
- To assist readers of the standard, a new Annex B has been added, tabulating which clauses in the standard apply to each separate category of fan. If you are familiar with either IEC 60079-15 or IEC 60079-11, you will have seen similar tables at the start of those documents.
- EN ISO 80079-36 and -37 were published last year. The new fan standard now makes reference to these international standards rather than the previous EN 13463 series. Among the requisite changes are the requirements for a new way of marking the fans.
Since the ISO 80079 series of documents are also available for use by IECEx, this poses the interesting question: can EN 14986 form the basis of true international certification, even though it is a European standard?
At SGS Baseefa, we believe the answer is: “Yes”.
It is fully recognised that published material from any source can be used to back up the “Ignition Hazard Assessment” required by ISO 80079-36. In this context, EN 14986 is a perfectly-valid document to use to aid the Ignition Hazard Assessment.
The IECEx certificate will, of course, be against ISO 80089-36 and -37, but the assessment process and reports can clearly be used to support both the IECEx certificate and the ATEX documentation.
With the availability of the new standards, we foresee that more and more manufacturers will use IECEx documentation as the basis for their ATEX Technical File and EU Declaration of Conformity, for both ATEX Category 3 Equipment and Non-Electrical ATEX Category 2 Equipment, where certification by a Notified Body is not mandated. Not only will the documentation form the Technical File for ATEX, but the IECEx certificate will provide documentation accepted in many places around the world.
For more information on how we can help you, please contact us on:
SGS is the world’s leading inspection, verification, testing and certification company. SGS is recognized as the global benchmark for quality and integrity. With more than 90,000 employees, SGS operates a network of over 2,000 offices and laboratories around the world.